Related Bylaws and Regulations
BRITISH COLUMBIA BUILDING CODE (BCBC) & Plumbing Code
The BC Building Code (BCBC) is a provincial regulation that governs the construction of new buildings, alterations & repairs to existing buildings, and demolitions are completed. The BCBC establishes minimal life safety, health, accessibility, fire, and energy requirements, and applies throughout the entire Province, with exemptions to lands under Federal jurisdiction, and the City of Vancouver.
The BCBC is freely available on the BC Codes website, and physical copies of the code can be purchased though the Queens Printers.
NEW WESTMINSTER BUILDING BYLAW
The New Westminster Building Bylaw provides additional construction requirements, including sprinklering of buildings and construction of swimming pools. The Bylaw also regulates the application, and issuance of building permits, and the conducting of site inspections throughout construction.
NEW WESTMINSTER ZONING BYLAW
The New Westminster Zoning Bylaw establishes requirements such as the types of uses permitted on a property, allowed density, building size and massing, and parking requirements.
BC ENERGY STEP CODE (BCESC)
The BC Energy Step Code is a compliance path within the BCBC, which the City of New Westminster has adopted to require a higher level of energy efficiency that is above the minimum prescribe requirements of the Building Code. BCESC requirements for new construction may include the involvement of a Certified Energy Advisor, completion of compliance forms for applications and inspections, and conducting blower door tests throughout construction. Please visit the Energy Save New West website for more information.
BC SOLAR HOT WATER READY REGULATIONS
The City of New Westminster has adopted the Provincial Solar Hot Water Ready Regulation (BC. 101/2011) for all single detached dwellings and detached accessory dwellings.
Requirements of this regulation include;
- two (2) conduit runs to an area on the roof with an area of not less than 9.3 sq. meters, and has no dimension less than 2.7 meters, to accommodate the future installation of a solar domestic hot water heating system in compliance with CAN/CSA-F383-87.
- Conduit runs must be accessible on both ends, capped and sealed to prevent air and water leakage, be identifiable by permanent markings, and have a minimum diameter of 50 mm.
- Structural roof members / roof trusses must be designed to accommodate a uniform dead load of 0.24 kPa, in addition to design loads required by the BCBC, and anticipated point loads.
For more information, please refer to the Provincial notices linked below;
- Guide to the Province of BC Solar Hot Water Ready Regulation 2013
- Solar Hot Water Ready Regulation - BC Reg. 101/2011
OTHER RELATED REGULATIONS
Other related building regulations, policies, and bylaws which a development may be required to comply to include, but are not limited to;